For tank level gauge probe is high-precision product, please take carefully when moving!
Please make sure the vertical of probe, otherwise will affect measure precision.
Don’t draw-off communication cable of probe when installation.
1. Take probe out of package box.
2. Record “Manufacturing Code” on nameplate of probe, in reserve for communication.
3. Remove foam package of probe
4. Install fixed plate at top and bottom of electric house.
5. Insert communication cable to the socket at top of electric house tightly.
6. Carefully put oil floater and water floater at the bottom of probe.
7. Insert probe into oil tank carefully by two hands, then hold fixed plate and adjust probe to be vertical, installation position please see Fig.
The cable from tank level gauge probe must be correctly coupled into relevant safety barrier inside console. The shielding of cable must be coupled into PE of safety barrier. The safety barrier also must be coupled into earth reliable.
1. Look for convenient place on the wall in office, to install tank gauge smart console.
2. Install the fixed plate of console tightly on the wall by expansion screw.
3. Hang tank gauge console on the fixed plate reliably.
4. The PE of console should be connected to earth reliably with more than 6 mm² multi-core copper soft cables.